Mon-Fri 8-4pm EST
This new addition to the General hospital was to be powered by the double ended substation from another building. The plan was to increase the size of the two transformers and switchgear in the main complex and run two 600 volt feeders to the new building.
By increasing the size of the existing transformers, it would also increase the fault levels in the existing building past what the panels could handle. This would mean replacing all the distribution.
Two loop feed liquid filled MiniSubs were installed in the existing electrical room with secondary breakers to protect the runs to the switchboard in the new building.
Cost saving of the whole project +300K
We are relocating! Come December 1st 2018 we will be in our new home in Elmira, Ontario. Find all the exciting details here! Dismiss